HFC R32 Products
LG R32 A2L (MILDLY FLAMMABLE) refrigerant range of Splits, Multi & Commercial AC Equipment (Up to 12kW)
WHY R32? is it Flammable?
High Global Warming Potential IF LEAKED BUT Non-FLAMMABLE
Current refrigerant for all systems (Splits, Multi Split and VRF ) since 2004. All in accordance with current F-Gas regulations and Health & Safety regulations (HSE). No bans (except split systems with a total charge of less 3kg) or end of line
Low Global Warming Potential IF LEAKED BUT FLAMMABLE
R32 refrigerants require special risk assessment as it is considered by HSE (Health & Safety Executive) as highly flammable. It falls under DSEAR (Dangerous Substances and Explosive Atmospheres Regulation) UK Regulations. or Europe ATEX
Important: F-Gas Regulations CANNOT cover any competence on SAFETY as it is primarily an Environmental qualification ensuring environmentally safe handling, NOT PERSONAL SAFETY.
Installers carry the ultimate responsibility and must
inform end-users of the Flammability Risks.
R32 can only be used in small applications (Max 12kW or less than 3kg charge per systems - outdoor, indoor and pipe works), (see F-Gas equipment sale ban by 2025 - NOT use) See F-gas Bans and LG Recommendations
It is the responsibility of the installer to ensure equipment have clear labeling and warning and are transparent to end-users, and emergency services. Building owners must ensure that their insurance providers are aware of the risks associated with flammable refrigerants.
LG R32 Equipment Range
Wall Mounted Splits (click to download)
Wall Mounted Splits Multi Splits Commercial split
Wall Mounted Multi Split Commercial
Engineering Data Book
Bans & Guidance
Guidelines, Recommendations & City & Guilds 6178 Training (installer safety)
AREA & EN378 standards FETA F-Gas Regulation
LG R32 Recomendations C & G 6187-21
This course covers all Hydrocarbon refrigerants, including handling of A3 hydrocarbons including R1270 Propylene, R290 Propane and R600a Isobutane. It is also suitable for engineers working with flammable HFO’s and HFC’s including R1234yf, R1234ze and R32
Protocols & Progress
Kigali Amendments UK Progress F-Gas AC Equipment Ban
- R32 is an HFC refrigerant Class A2L (A2L not Used in Large (greater than 3 kg system charge) Splits, Multi splits, VRF or Chiller systems ). It is not a long-term refrigerant, cannot be dropped in, requires Specific Risk Assesment unders DSEAR, require extra training (installer safety) to handle flammables e.g. City & Guilds 6187-21 and require specific guidelines (see LG installation recommendations).
- R410A or R134a or R407C are HFC refrigerants (common Air Conditioning refrigerants which are A1classified (non Flammable), used in Splits, Multi, Commercial, VRF, Chillers, Roof Tops ) - (See F-Gas 2014 Regulations Specifically point 3 (new HFC ban)
the final solution? :
There two regulations that affect the reduction of current HFC refrigerants with high GWP.
The European F-Gas and the Kigali Amendments to Montreal Protocole.
None of them is legally binding and there is no phase-out, and both rely on the future innovation of new Lo GWP refrigerants and equipment manufacturers ensuring no waste and better control on leakage (40 % of refrigerants used in AC/ Refrigeration is used in servicing). see links to both.
An important website to find out more we highly recommend: http://www.gluckmanconsulting.com
Space Air Web Site will have more guidance and advice to ensure the correct & Safe use of LG AC equipment utilising R32 Refrigerants. Including FACTS & FIGURES
Space Air Terms & Conditions